UHO-3 Bracket | FlexHead Industries
Home / Products / Commercial / UHO-3 Bracket
The FlexHead® UHO-3 mounting bracket can be installed with 3/8″ or ½” threaded rod attachments. The 3/8″ rod is FM Approved to be installed up to 4ft off the structure and the 1/2″ threaded rod up to 6ft of the structure.
The UHO-3 bracket is ideal for providing fire protection in unfinished spaces. Once the suspended ceiling in installed, simply remove the FlexHead® hose from the UHO-3 bracket and install in into a suspended ceiling bracket then reuse the UHO-3 on your next shell job, saving both time and money!.
UHO-3 bracket: G90 galvanized steel
1/2″ or 3/8″ threaded rod (not included)
Friction Loss Data and Specifications for UHO-3 Bracket
Max # of 90-degree Bends
FM Max Equivalent Length of Sch 40
Maximum Ambiet Temp Rating
Max Rated Pressure H-Series psi (kpa) / psi (kpa)
Model Numbers: The "H" designates high pressure unit rated to 300 psig and the "E" designates elbow style unit. *FM Bend Radius 8"
When ordering, UHO-3 bracket model must be specified
in (cm) ft (cm) 8" Bend Radius Nom 1 in Diameter Pipe, ft FM
2024, 2024H 1?2 (1.27) 2 (0.6) 3 18.4 300º (148º) 175 (1205) / 300 (2068)
2036, 2036H 1?2 (1.27) 3 (0.9) 3 26.6 300º (148º) 175 (1205) / 300 (2068)
2048, 2048H 1?2 (1.27) 4 (1.2) 4 30.3 300º (148º) 175 (1205) / 300 (2068)
2060, 2060H 1?2 (1.27) 5 (1.5) 4 35.8 300º (148º) 175 (1205) / 300 (2068)
2072, 2072H 1?2 (1.27) 6 (1.8) 4 45.6 300º (148º) 175 (1205) / 300 (2068)
2024, 2024H 3?4 (1.90) 2 (0.6) 3 14.7 300º (148º) 175 (1205) / 300 (2068)
2036, 2036H 3?4 (1.90) 3 (0.9) 3 21.8 300º (148º) 175 (1205) / 300 (2068)
2048, 2048H 3?4 (1.90) 4 (1.2) 4 29 300º (148º) 175 (1205) / 300 (2068)
2060, 2060H 3?4 (1.90) 5 (1.5) 4 36.1 300º (148º) 175 (1205) / 300 (2068)
2072, 2072H 3?4 (1.90) 6 (1.8) 4 43.2 300º (148º) 175 (1205) / 300 (2068)
175 psi 300 psi
2024E, 2024HE 1?2 (1.27) 2 (0.6) 3 26.4 14.7 300º (148º) 175 (1205) / 300 (2068)
2036E, 2036HE 1?2 (1.27) 3 (0.9) 3 30.1 21.8 300º (148º) 175 (1205) / 300 (2068)
2048E, 2048HE 1?2 (1.27) 4 (1.2) 4 33.8 29 300º (148º) 175 (1205) / 300 (2068)
2060E, 2060HE 1?2 (1.27) 5 (1.5) 4 37.5 36.1 300º (148º) 175 (1205) / 300 (2068)
2072E, 2072HE 1?2 (1.27) 6 (1.8) 4 41.2 43.2 300º (148º) 175 (1205) / 300 (2068)
2024E, 2024HE 3?4 (1.90) 2 (0.6) 3 14.7 14.7 300º (148º) 175 (1205) / 300 (2068)
2036E, 2036HE 3?4 (1.90) 3 (0.9) 3 21.8 21.8 300º (148º) 175 (1205) / 300 (2068)
2048E, 2048HE 3?4 (1.90) 4 (1.2) 4 29 29 300º (148º) 175 (1205) / 300 (2068)
2060E, 2060HE 3?4 (1.90) 5 (1.5) 4 36.1 36.1 300º (148º) 175 (1205) / 300 (2068)
2072E, 2072HE 3/4 (1.90) 6 (1.8) 4 43.2 43.2 300º (148º) 175 (1205) / 300 (2068)
M ( May 24 )
UHO-3 Bracket | FlexHead Industries
Home / Products / Commercial / UHO-3 Bracket
The FlexHead® UHO-3 mounting bracket can be installed with 3/8″ or ½” threaded rod attachments. The 3/8″ rod is FM Approved to be installed up to 4ft off the structure and the 1/2″ threaded rod up to 6ft of the structure.
The UHO-3 bracket is ideal for providing fire protection in unfinished spaces. Once the suspended ceiling in installed, simply remove the FlexHead® hose from the UHO-3 bracket and install in into a suspended ceiling bracket then reuse the UHO-3 on your next shell job, saving both time and money!.
UHO-3 bracket: G90 galvanized steel
1/2″ or 3/8″ threaded rod (not included)
Friction Loss Data and Specifications for UHO-3 Bracket
Max # of 90-degree Bends
FM Max Equivalent Length of Sch 40
Maximum Ambiet Temp Rating
Max Rated Pressure H-Series psi (kpa) / psi (kpa)
Model Numbers: The "H" designates high pressure unit rated to 300 psig and the "E" designates elbow style unit. *FM Bend Radius 8"
When ordering, UHO-3 bracket model must be specified
in (cm) ft (cm) 8" Bend Radius Nom 1 in Diameter Pipe, ft FM
2024, 2024H 1?2 (1.27) 2 (0.6) 3 18.4 300º (148º) 175 (1205) / 300 (2068)
2036, 2036H 1?2 (1.27) 3 (0.9) 3 26.6 300º (148º) 175 (1205) / 300 (2068)
2048, 2048H 1?2 (1.27) 4 (1.2) 4 30.3 300º (148º) 175 (1205) / 300 (2068)
2060,
 2060H 1?2 (1.27) 5 (1.5) 4 35.8 300º (148º) 175 (1205) / 300 (2068)
2072, 2072H 1?2 (1.27) 6 (1.8) 4 45.6 300º (148º) 175 (1205) / 300 (2068)
2024, 2024H 3?4 (1.90) 2 (0.6) 3 14.7 300º (148º) 175 (1205) / 300 (2068)
2036, 2036H 3?4 (1.90) 3 (0.9) 3 21.8 300º (148º) 175 (1205) / 300 (2068)
2048, 2048H 3?4 (1.90) 4 (1.2) 4 29 300º (148º) 175 (1205) / 300 (2068)
2060, 2060H 3?4 (1.90) 5 (1.5) 4 36.1 300º (148º) 175 (1205) / 300 (2068)
2072, 2072H 3?4 (1.90) 6 (1.8) 4 43.2 300º (148º) 175 (1205) / 300 (2068)
175 psi 300 psi
2024E, 2024HE 1?2 (1.27) 2 (0.6) 3 26.4 14.7 300º (148º) 175 (1205) / 300 (2068)
2036E, 2036HE 1?2 (1.27) 3 (0.9) 3 30.1 21.8 300º (148º) 175 (1205) / 300 (2068)
2048E, 2048HE 1?2 (1.27) 4 (1.2) 4 33.8 29 300º (148º) 175 (1205) / 300 (2068)
2060E, 2060HE 1?2 (1.27) 5 (1.5) 4 37.5 36.1 300º (148º) 175 (1205) / 300 (2068)
2072E, 2072HE 1?2 (1.27) 6 (1.8) 4 41.2 43.2 300º (148º) 175 (1205) / 300 (2068)
2024E, 2024HE 3?4 (1.90) 2 (0.6) 3 14.7 14.7 300º (148º) 175 (1205) / 300 (2068)
2036E, 2036HE 3?4 (1.90) 3 (0.9) 3 21.8 21.8 300º (148º) 175 (1205) / 300 (2068)
2048E, 2048HE 3?4 (1.90) 4 (1.2) 4 29 29 300º (148º) 175 (1205) / 300 (2068)
2060E, 2060HE 3?4 (1.90) 5 (1.5) 4 36.1 36.1 300º (148º) 175 (1205) / 300 (2068)
2072E, 2072HE 3/4 (1.90) 6 (1.8) 4 43.2 43.2 300º (148º) 175 (1205) / 300 (2068)
M ( May 24 )